Rika is a sensor manufacturer & solution provider of environmental and weather monitoring for 10+ years
What factors should be paid attention to in the environmental monitoring system of the data center computer room?
With the development of information technology, the number of computer systems and communication equipment is increasing day by day, and the scale is getting bigger and bigger. Central computer rooms, IDC, etc. have become the core places for business management of major units. However, these places are of different scales and scattered in various places, and the types and quantities of equipment in them are numerous, and due to the lack of matching management methods, the physical environment in the computer room may be in emergency at any time. The environmental safety of the data center computer room is an important guarantee for the stable operation of the overall system of the computer room. The environmental requirements of the data center computer room are not only related to the normal operation and failure rate of the computer room, but also related to the physical and mental health of the staff in the computer room. For everyone to explain in detail what factors and requirements should be paid attention to in the data center computer room environmental monitoring system? 1. Air conditioning requirements (the key to energy saving in data centers) Article 22.214.171.124 of the computer room site national standard GB2887-89 computer station site technical conditions stipulates the ambient temperature and humidity standards in the computer room when it is turned on. The ambient temperature is: Class A 22±2°C, Class B 15-30°C, Class C 10~35°C; Environmental humidity: Class A 45%-65%, Class B 40% ～70%, C level 30%～80%; The standard of general communication equipment room should reach the A level standard. 2. Requirements for air supply IT equipment requires 150~595m³/h air flow per KW power consumption (calculated by temperature rise). The air conditioner must meet the requirements of the rack, otherwise it will cause the rack to inhale its own exhaust air and eventually cause overheating. 3. Requirements for the fresh air system The purpose of fresh air is to maintain the positive pressure in the computer room; the purpose of maintaining the positive pressure in the computer room is to ensure the cleanliness and relative humidity of the computer room. The more versatile fresh air unit has the functions of filtering outdoor air, humidifying, dehumidifying, cooling and heating. 4. Requirements for static electricity The electrostatic potential of the insulator in the host room should not be greater than the electrostatic leakage resistance of the ground of the machine room and the electrostatic potential of the insulator should also comply with relevant regulations. 5. Requirements for noise When the computer system is shut down, the noise in the computer room should be less than 6SdB(A) when tested at the center of the host room. 6. Requirement of contrast The computer room is 0.8m from the ground, and the illuminance should not be less than 3001x, and the illuminance of the auxiliary room should not be less than 2001x. 7. Requirements for cleanliness Air cleanliness: particles larger than 0.5μm in each liter of air should be less than 18,000 particles. (Grade A)8. Requirements for harmful gasesSulfur dioxide≤0.15mg/m³, hydrogen sulfide≤0.01mg/m³ (Grade A)Sulfur dioxide≤1mg/m³, hydrogen sulfide≤ 0.1mg/m³ (Grade B)At an ambient temperature of 25±5℃ and a relative humidity of 40%~80%. 9. Requirements for the continuity of the air conditioning and refrigeration system After the air conditioner is out of operation, the IT equipment can continue to operate using the cold air heat in the room. The UPS air conditioner can provide a larger circulating air volume (generally the construction of the computer room is completed, During the test, the temperature rise test will be carried out; the temperature rise of the computer room can also be obtained by calculation; in general, it can be compared with the temperature rise test of the dummy load.)10. Requirements for radio interference field strength When the frequency is 0.15~1000MHz, it is not more than 126dB. 11. Requirements for magnetic field interference The field strength of magnetic field interference is not more than 800A/m, and it must be set according to the specified size. 12. Requirements for floor vibration acceleration value Under the condition of computer system shutdown, the vertical and horizontal vibration acceleration value of the floor surface of the host room should not be greater than 500mm/s. 13. Requirements for resistanceThe electrostatic leakage resistance of the floor and work surface of the host room should meet the requirements of the current national standard GE6650-1986 'Technical Requirements for Raised Floors for Computer Room'.
Hunan Rika Electronic Tech Co.,Ltd thinks that customer satisfaction is one of the most important determinants of brand loyalty. High-quality service can be the difference between a one-time buyer and a lifelong repeat customer.
At the heart of sensor solution is our Vision to be the global energy company most admired for its people, partnership and performance.
Looking for Manufacturers in China? Then Hunan Rika Electronic Tech Co.,Ltd is the right choice. we are a well known OEM sensor sensor solution Manufacturers and suppliers from China.
Our company is professional in manufacturing sensor solution especially environmental monitoring systems.